Indoor and outdoor fire hydrant is very important in life, but its application also has different requirements. For example, the water output of each outdoor fire hydrant is calculated as 10 ~ 15L / s, and the outdoor fire hydrant shall be evenly arranged, not concentrated on the side of the building, etc.
The equipment can be set in places such as civil air defense engineering, with a distance of not less than 5m and not more than 40m from the entrance and exit; some outdoor fire hydrants are set near the parking lot, with a distance of not less than 15m from the gas station or depot.
Indoor fire hydrant system is set in many places, but some can't. fire hose can be installed:
① Single and multi-layer D and e plants (warehouses) have low flammability.
② Class D plant with fire resistance rating of 3 and 4 and building volume of no more than 3000m3; class E plant (warehouse) with fire resistance rating of 3 and 4 and building volume of no more than 5000m3.
③ The granary, treasury and independent buildings are far away from the town and unattended.
Above about indoor and outdoor fire hydrant related introduction, if you still have questions, you can directly consult us!